On April 20, 2018, customers sent two live videos, DN1400 rubber soft connector, one appeared torsion phenomenon, the other was normal, with contrast, customers reported that the product was deformed.
Reason analysis: The product is twisted by external force in the process of using, and the phenomenon of twisting is strictly prohibited in the process of using rubber soft joints. The following accessories have a temporary test done by our factory: the phenomenon of twisting rubber soft joints caused by external force.
The manufacturer's suggestion: adjust the pipeline, make the twisted pipeline turn back, and reinstall the limited fixture attached to our factory.
Above is a written analysis report provided by the Technical Department of our factory. If you have any questions, you can call the road worker: 15921366665. Thank you.
Here are the live photos: